**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**A**

**Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility**

The consequence-frequency assessment methodology (see Chapter 6) can be illustrated by example. For the purpose of this discussion, only advanced wastewater treatment facilities subsequent to secondary wastewater treatment are considered. For acute contaminants (such as microorganisms), the influent stream to such a facility may be highly variable. For example, at Water Factory 21, the range in influent virus levels was more than two orders of magnitude, and the distribution could be roughly described by a log normal distribution (see Figure A-1).

A given facility may have a sequence of processes individually capable of changing the microbial distribution. Figure A-2 depicts such a treatment in general terms. The concentrations of pollutants (e.g., viruses) at each stage of treatment are given as *C _{0}, C_{1}, C_{2},* and so on. The connection between individual concentrations is given by a conditional distribution. For example,

*F*

_{2}(C_{2}C_{1}) is the probability density of virus following filtration, given the virus concentration entering the filter. In other words, if the filter influent contains a virus concentration C

_{1}then the integral

gives the probability that the filter effluent will contain a virus concentration between . Where the processes behave in a linear (first-order) fashion, this distribution may be written simply in terms of the

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

ratio of the effluent to influent concentration; however the conditional framework (as shown in Figure A-2) provides a more general approach Formally the probability distribution of the product concentrations may be evaluated as a multiple integral, which can (for the indicated process train) be written as (Stuart and Ord, 1987)

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

For compactness, the arguments for the conditional distributions are omitted in this integral. Analytical evaluation of this integral may not be possible in many (perhaps most) cases. Therefore the problem must be approached numerically, and there are at least two numerical approaches to the problem. In one approach, the deterministic function connecting *C _{0}* and

*C*is written:

_{5}If the moments (mean, variance, etc.) of the influent distribution *(C _{0})* and the process removal

*(C*distributions, along with any correlations, are known, then the moments of the quantity ln

_{i}/Ci-_{1})*(C*can be computed using propagation methods (Ku, 1966). However, this method is algebraically complex, and unless further assumptions are made, it cannot directly produce confidence distributions.

_{5})The Monte Carlo method is an alternative that is widely employed in risk assessment (Burmaster and Anderson, 1994; Finkel, 1990; Haas et al., 1993; Smith, 1994). In this approach, each of the distributions is sampled repeatedly, and the final concentration is computed for each set of random samples. By repeated sampling, the distribution of final concentrations is obtained.

To employ either of these methods, information about the transformation probability distributions must be obtained or assumed. For example, in the Water Factory 21 project (James M. Montgomery Consulting Engineers, 1979), paired samples of influent and clarified lime-treated water were analyzed for viruses. The resulting data are presented in the two panels of Figure A-3. It would appear that the removal in this process can be characterized by a log normal distribution of a removal efficiency (effluent/influent); however, the low number of data points does not provide a powerful test of alternative models. (For example, is removal efficiency dependent in a systematic manner on the influent viral loading or on other process descriptors such as pH?)

Obtaining information on process removal distributions is a data-intensive task. The actual data in Figure A-3 span from 10 to 90 percent cumulative probability. The implementation of a full Monte Carlo analy-

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

sis would require fitting this distribution to a particular form, which can then be used to extrapolate beyond the ''tails" of the observed data. There are an infinite number of potential distributions. While the log normal has most frequently been used, the gamma and pareto may also have particular utility in the description of relatively rare failure distributions. The degree to which the choice of a particular distributional assumption influences the results of a Monte Carlo calculation has not been well studied, although preliminary results suggest that the choice of distributional form may not be overly crucial except in very highly skewed situations.

In principle, if the data on process performance distributions are available, then the probability distribution of a particular contaminant in the water to be ingested may be estimated. The final results may be presented as Figure A-4. Results from hypothetical data are plotted on a Weibull scale, which would result in a linear plot if the Weibull distribution provided a good fit to the data. From this figure one could estimate, for example, that there would be exposure to 10^{-3} plaque forming units per day more than 1 percent of the time. This information may be com-

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

bined with a dose-response assessment to ascertain the likelihood of a risk of infection or illness of a given magnitude.

**References**

Burmaster, D. E., and P. D. Anderson. 1994. Principles of good practice for the use of Monte Carlo techniques in human health and ecological risk assessment. Risk Analysis 14(4): 477-481.

Finkel, A. M. 1990. Confronting Uncertainty in Risk Management. Washington D.C.: Resources for the Future, Center for Risk Management.

Haas, C. N., J. B. Rose, C. P. Gerba, and S. Regli. 1993. Risk assessment of virus in drinking water. Risk Analysis 13(5):545-552.

James M. Montgomery Consulting Engineers. 1979. Water Factory 21 Virus Study, Orange County Water District. New York: John Wiley.

Ku, H. 1966. Notes on the use of propagation of error formulas. Journal of Research of the National Bureau of Standards-C: Engineering and Instrumentation 70C(4):263-273.

Smith, R. L. 1994. Use of Monte Carlo simulation for human exposure assessment at a Superfund site. Risk Analysis 14(4):433-439.

Stuart, A., and J. K. Ord. 1987. Kendall's Advanced Theory of Statistics. New York:Oxford University Press.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.

**Suggested Citation:**"Appendix A: Use of Consequence-Frequency Assessment to Evaluate Performance of an Advanced Wastewater Treatment Facility." National Research Council. 1998.

*Issues in Potable Reuse: The Viability of Augmenting Drinking Water Supplies with Reclaimed Water*. Washington, DC: The National Academies Press. doi: 10.17226/6022.